Kair KHRV150 Single Room Heat Recovery Ventilation Fan
|Delivery Options Available For This Product – inclusive of vat|
|Pick Up From Store||FREE|
|3 – 5 Day Economy||FREE|
|Next Day Delivery (8AM – 6PM)||Minimum £10.2 for this product.|
|Next Day AM (Anytime Up To 12PM)||Minimum £18 for this product.|
|Next Day Before 10.30AM||Minimum £25.2 for this product.|
|Saturday Next Day||Minimum £21.6 for this product.|
|Sunday Next Day||Minimum £21.6 for this product.|
|Northern & Southern Ireland 2 Day Service||Minimum £20.4 for this product.|
|Scottish Highlands 2-4 Days Service||Minimum £19.2 for this product.|
|Same Day Delivery||Minimum £12.50 for this product.|
|Same Day AM Delivery||Minimum £20.00 for this product.|
|Isle of Wight Delivery||Fixed £20.00 inc VAT for this product.|
£285.00 (inc vat)
– Whisper quiet
– Night sensor mode, (will not operate boost mode at night. Ideal for bedrooms)
– Pullcord over-ride
– 2 fan speed settings
– Tamper proof humidistat control (requires tamper proof bit for installation and maintenance) for Tenanted properties.
– Humidity adjustment control
Guaranteed to prevent condensation in the room it’s installed in. Energy efficient, recovers up to 86% of the heat in the room.
Alliance Remedial Supplies highly recommend this product to Landlords, Damp Proofers and Builders.
This product should be installed by a suitably qualified electrician to an independent fused spur.
Follow the instruction guide which comes in the packaging.
This product is not suitable for ducting. It should only go out directly through and external wall. A 1 meter extension duct kit is available separately for thick walls. Trim ducting to length required.
Carry out a survey of the external wall to select suitable installation position.
Avoid any structural details such as Lintels, Cavity Trays, Soldier Course, Guttering downpipe, external plumbing, etc. Do not install close to a window opening in the room the fan is intended to go in. Install no less than 600mm away from boiler flues.
Use a 152mm diamond core drill bit to core the hole for the fan. Drill a 2 – 3mm downward incline to allow condensate to run out the external cowl.
If the fan is going into a tenanted property we recommend using the 3 x tamper proof screws included in the packaging to prevent humidity sensor settings from being adjusted after installation. You will require a tamper proof drill bit or tamper proof screwdriver to use these screws.
In high humidity rooms such as bathrooms we suggest setting the humidity sensor at 60%. In Living areas we recommend setting between 55- 60%.
Replace the black humidity setting wheel with the white blanking tab in the packaging and place the wheel inside the humidity sensor case or keep safe for any future adjustments.
Standard delivery is free of charge 3 – 5 day economy service. We cannot offer a delivery day or time within this service. You can upgrade your delivery service from our menu of delivery services including next day, next day am.
Please allow plenty of time for materials ordered for a specific job at a specific time and day as we cannot guarantee third party delivery services. Please allow plenty of time for your order to be with you in good time.
Please read our delivery terms and conditions ahead of ordering.